- Water Filter Systems
Reverse Osmosis Filter
- Gallons Per Day
- System Ratio Waste:Clean
2:1 - 1:1
- Recommended Feed Pressure
Achieve the highest flow rates from the Hydro-Logic Evolution 1000, the most efficient RO system on the planet! The Evolution-RO is capable of producing more than 1,200 GPD or 50 gallons per hour of pure water. Remove 95%+ of all parts per million from your tap water. Save more water by running 2:1 waste to product water ratio; now includes 1:1 ratio as an option (to save 50% of the waste water). The Hydro-Logic Evolution has a simple and quick setup, with no electricity needed unless you buy the booster pump accessory.
The Evolution-RO Reverse Osmosis System produces up to 1200 GPD (gallons per day) of ultra-pure, low PPM water. This beast removes 95%+ of all contaminants and chlorine without wasting any water.
SAVE MORE WATER by running a 2:1 waste to product water ratio, or optional 1:1 ratio (included)
Includes ChloraShield™ carbon filter for 100% chloramine removal
Evolution-RO Unit Includes:
- 9. (x1) Pressure Gauge w/ Tee fitting
- 10. (x1) Support Leg/Housing Wrench
- 11. (6 ft.) 1/2" Inlet White Tubing
- 12. (10 ft.) 3/8" Waste Black Tubing
- 13. (10 ft.) 3/8" Outlet Blue Tubing
- 14. (x1) Garden Hose Connector
- 15. (x1) Inline Shutoff Valve
Everthing included with this product is all you need to get started on your way to cleaner water for your plants
Below we will go into detail about some Add-Ons & Accessories that will truly bring you into the 21st century of water filtration
Add-Ons & Accessories
Pre-Evolution High Capacity Pre-Filter
Ensure your Evolution-RO runs more efficiently. Helps protect the RO membranes and extends their life. Less filter changes and maintenance - every 7,500 gallons of purified water. Cleanable sediment filter is re-usable. Combination of KDF85 and the KDF55 with eco-friendly catalytic carbon filter reduces chlorine, chloramines, iron, sulfur, and heavy metals. - great for city or well water. Highly recommended when using more than 150 gallons of purified water per week on average.
All Evolution-RO add-ons & accessories are available seperately and can be added to your cart at the top of the page.
Replacement Filters, Membranes, & Housings for Evolution-RO
Replace after 5,000 Gallons
Replace when PPM Increases
Replace after 3 Years
- Product Water Flow Rate: 1,200 GPD/50 GPH
- Materials of Construction: High durability polypropylene construction provide years of dependable service
- Average Permeate Flow Rate: 0.83 Gallons/Minute, 50 Gallons/Hour, or 1200 Gallons/Day
- Uses Line Pressure: >60 psi. Pump recommended with all Evolution purchases because the Evolution operates best at 60 psi (max pressure is 80 psi)
- Average TDS Rejection: 95+%
- RO Membrane (H x D) (The Evolution uses 2 Membranes): 18.75" x 3.16"
- Waste to Purified Water Ratio: 2:1 or 1:1
- Dimensions (H x W x D): 13" x 23" x 13"
- Weight: 21.40 lbs
- Evolution-RO™ filter housings must be replaced every 3 years
- Filter replacement schedules for Reverse Osmosis carbon filters based on product water
- Water Filter Systems
- Tech Specs
Brand Hydro Logic SKU HL31023 Weight (lb.) 21.4 Height (in.) 12.8 Width (in.) 12.9 Length (in.) 23.2 Warranty 1 Year Lead Time Due to social distancing requirements, this item ships in 3 weeks UPC 812111011567 Prop 65 No Gallons Per Day 1,000 System Ratio Waste:Clean 2:1 - 1:1 Inlet Tubing Size 1/2" Product Tubing Size 3/8" Waste Tubing Size 3/8" Gallons Per Hour 50 Min. Feed Pressure 60 PSI Recommended Feed Pressure 60-80 PSI Operating Temperature 40-100F Operating pH 4-10 Nominal % Rejection 95+ Max TDS 1,000 PPM Max Hardness 171 mg/L (10 grain) Voltage N/A
Hydro Logic Evolution-RO High Flow RO System, 1200 GPD Videos
Flushing a KDF Carbon filter►
- Product Q&A
Hydro Logic Evolution-RO High Flow RO System, 1200 GPD Questions & Answers
I have well water, what challenges can I expect?
Here are the most common challenges when filtering well water:
- Well water is typically colder which will decrease your flow rates because cold water flows slower through a reverse osmosis membrane.
- Well water often has higher PPM/TDS levels (hardness) which can decrease the life of a membrane
- Well water can contain high levels of sediment which can easIly clog a carbon or sediment prefilter.
- Well water can have high levels of iron, manganese and hydrogen sulfide (rotten egg smell).
- Well water occasionally contains iron bacteria which is difficult to remove.
- Well water generally has low water pressure.
How does reverse osmosis affect pH?
RO product water can have a lower pH than the feed water. It depends on the level of dissolved CO2 in the feed water. A lowering of pH can ocurr because the existing CO2 in the water, being a gas, passes through the membrane but the alkaline constituents, primarily HCO3 (bicarbonate), are removed as part of the reject water. In the feed water the HCO3 neutralizes the acid-causing CO2. In the product water, with HCO3, greatly reduced, the CO2 is free to combine with the H2O to form carbonic acid: CO2 + H2O > H2CO.
Another reason to question the pH reading is that for any water sample which is very low in TDS it is very hard to obtain an accurate pH value. The worst case of this accuracy problem occurs with de-ionized water but some low TDS RO water will react the same. The sample is so low in minerals that there is no buffer. The slightest absorption or loss of CO2 shifts the pH substantially. The water’s tendency to pick up additional CO2 from the ambient air, even if the test is done on site, can produce a very low false pH.
In reality, measuring the pH of RO water is difficult and not accurate due to lack of any pH buffering the RO water. If the feed water has a lot of dissolved CO2 then pH can drop a few points. But, in the case of a drinking water RO system, a post re-mineralization filter will help neutralize the final product water's pH level. In the case of RO water for horticultural purposes, once you mix a calcium/magnesium supplement into the RO water and then add your nutrients and additives, the final pH can be adjusted and your feed formula should be pH stable.
Why do pH levels come out higher than the source water when running water through a carbon or Carbon/KDF filter?
This is common, there is generally a significant pH spike from the GAC (granular activated carbon) that is mitigated relatively quickly after start up. For some systems, it can take days or even weeks to run enough rinse water to get the pH back to normal. Since it is temporary, it is generally not a significant issue.
Can the Evolution RO1000 be used as a drinking water system for my home?
The Evolution is not really designed to be an under the sink drinking water system. The reason for this is because the large membranes in that system perform what is called “TDS creep”. This means upon system start up the ppm’s will come out higher for a minute or two and then go back down to the 94/95% ppm rejection that is standard. This happens because there is untreated water in the membranes/housings from the last time you ran the system and then shut it off. When filling a 50 or 100 gallon reservoir this really is insignificant as it evens out with the rest of the purified water. One option for using the Evolution for drinking water is to use it to fill 5 gallon jugs and put them on a water dispenser (like the ceramic ones). We also have post-remineralization filters that polish the flavor that can be perceived as flat to some people. The remineralization filter adds soluble calcium and makes the water more alkaline and sweetens the flavor a bit. We also have a system that is specifically designed as an under the sink drinking water system. This is called the Ecospring. There is also the option to turn a Stealth 100 or 200 into a drinking water system by purchasing the Stealth drinking water upgrade kit.
How do I properly store a Reverse Osmosis System that won't be used for more than 3 weeks
Reverse osmosis membranes like water to run through them often in order to perform properly. Running water for once a day for a short period of time is ideal, but even once a week is sufficient. If you are not going to use your reverse osmosis system for 3-4 weeks or longer, there are storage procedures you should follow to maintain optimum system performance. Take the membrane(s) out of the system and place in a plastic bag and put them in the refrigerator. A white plastic kitchen bag with a knot tied at the top works well. Take the carbon filter(and in some systems such as the Stealth 100/200 the sediment filter as well) out of the housing and let it(them) dry out. Leave the housings and the caps on the system unscrewed to let them dry out. The purpose of this is to not trap wet filters and moisture in the system so that bacteria will not grow. As an extra measure of precaution, sterilizing using a light bleach or hydrogen peroxide solution to clean the housings, tubing and fittings is a good idea before using the system again.
How do I know if I have iron in my water?
If your carbon or sediment filter appears to be red, maroon, orange or brown in color you have iron in your water. You may also notice that your sinks and or toilets also have this discoloration. See an example image below of a system that was used to filter water with excessive iron levels.
Hydro Logic Evolution-RO High Flow RO System, 1200 GPD Reviews
- The product completely saved my family.
As a farmer I am dependent on a clean water source. Recent activities at nearby wineries changed the chemical balance of our shared water table. On many of our delicate herbs which we depend on for our living the water became toxic reading out close to 900 ppm. I thought my crop was a total loss but upon purchasing this device it saved my crop and subsequently my family.
- Great filter
I love this
- Great price and quality product
I use this when I need to refill my reservoir when I change out my nutes in my Under Current. One of the best priced on the market for this size and it was very easy to set-up. John was very knowledgeable when I called in with some questions and it arrived fast. Thanks!